LED Refrigerated Display Case Lighting Specification
The LED Refrigerated Display Case Lighting Specification delivers nearly 50% energy savings compared to a typical display case lighting code. If all retail refrigerated display cases switched to light-emitting diode (LED) systems today, 2.1 terawatt-hours (TWh) of electricity could be saved annually.
LED technology is advancing into new categories of white light applications, including refrigerated display case lighting. In September 2009, a BBA working group formed to investigate the use of LED refrigerated display case lighting for retail buildings.
Although LED technology is progressing, some barriers exist to mass adoption of LEDs. At present, performance in the later years of the product's lifetime can only be estimated and LED luminaires are relatively expensive on a first-cost basis.
To address these issues, members of a BBA working group investigated the use of LED refrigerated display case lighting. In coordination with the DOE and the Pacific Northwest National Laboratory, they have developed product performance specifications and evaluation procedures based on BBA member needs.
The following points detail information about the specification:
- Efficacy is evaluated in terms of the actual luminaire(s) load imposed on a given power supply. Power supply efficiency is negatively affected by under-loading, which occurs when the total wattage of luminaire(s) fed by a power supply is significantly lower than the power supply's rated wattage. This effect is captured via the power supply schedule, which lists the efficacy of every configuration installed on a given project.
- Useful life is evaluated in terms of warranty period, not on manufacturer projections.
- LED device manufacturers are required to perform industry-standard reliability testing.
- Rather than relying on field measurements, luminaires are tested in a controlled independent lab environment per LM-79 for consistency and slightly understated output.
- Because many luminaire designs preclude the use of standard far-field photometry in these applications, near-field photometry is mandated to accurately assess uniformity.
- To ensure acceptable rendition of saturated colors in product packaging, requirements for special indices R9 through R12 are included as a supplement to the color rendering index (CRI).
- Although a recommendation for minimum light levels is offered, criteria are structured to allow for flexibility in the selection of appropriate light levels on a project-by-project basis.
Several luminaire types and corresponding case geometries are addressed, as indicated in the figure below:
The following table shows some of the benefits of using LEDs in refrigerated cases:
|Product Feature||LED Benefits|
|Uniformity||Smaller sources allow for improved beam control and even illumination|
|Visual Comfort & Focus||Stray light and glare are reduced, allowing focus on merchandise|
Inherent directionality of LEDs reduces internal losses
LED efficacy improves at lower temperatures
Light is not wasted in non-uniform "hot spots"
Wide dimming range allows for increased energy savings
|Maintenance||Very low maintenance expected due to long life and durability|
|Disposal||Contains no mercury|
Popular Commercial Links
July 30, 2014
July 30, 2014
September 9, 2014
September 11, 2014